|Place of Origin:||China|
|Certification:||IS09001, IS014001,OHSAS18001 CCC|
|Minimum Order Quantity:||Negotiable|
|Packaging Details:||New Wooden drum, reel, circle, or according to customers request.|
|Delivery Time:||800 kilometer / kilometers per month conductor.|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||According to customers request, usually 2-4 weeks.|
|Material:||Steel & Aluminum||Life Span:||More Than 30 Years|
|Voltage:||Medium||Port:||Qingdao / Shanghai|
4 AWG Aluminium Conductor Steel Reinforced,
ASTM-B232 Aluminium Conductor Steel Reinforced,
4 AWG acsr dog conductor
Bare Aluminium Conductor Steel Reinforced
ASTM-B232 Standard specification for Concentric-Lay-Stranded Aluminum 1350 Conductors
BS215-2 aluminum conductors steel-reinforced —For overhead power transmission
DIN48204 Steel reinforced aluminum stranded conductors
IEC209 Aluminum stranded conductor steel reinforced
We could produce most of the standards cables, such as ASTM, BS, CSA, DIN, GB and IEC standards, etc.
|Code||Size (AWG/MCM)||Number of Strands(mm)||Weight(kg/km)||Rated Strength(kg)|
Used bare overhead transmission cable and as primary and secondary distribution cable acsr offers optimal strength for line design without sacrificing ampacity.
ACSR is a composite concentric-lay-stranded conductor. Galvanized steel strand or strands form the central core of the conductor,around which is stranded one or more layers of EC Grade Aluminum wires. The steel core may consist of a single strand or a concentricstranded cable of 7, 19, 37, or more wires. Numerous combinations of aluminum and steel strands and layers are possible. If you haveany suggestions or opinions about our products,please leave a message,and we will immediately answer your questions. Thanks for your support.
(1). The permissible long-time operating temperature for aerial conductor is 70℃.
(2). Under the circumstance that rare climate is occurring and ice coverage rate low in heavy ice area, the biggest stress of cable at the lowest point of the sag should not exceed 60% of the short-time destructive power.
(3). When connecting conductors, the conductor beside the connecting tube cant be prominent. Otherwise, the force on the operating conductors will be unbalanced. After connectors are install, the connecting tube should be painted by moisture-proof varnish in order to protect it from corrosion.
(4). Under installation, the arc downing stress of all the conductors should be the same. With in the permissible distance of crossing buildings or dropping to the ground, the stress can be 10-15% higher than regular stress.
Contact Person: Alex Yang