|Place of Origin:||Henan|
|Minimum Order Quantity:||1000M|
|Packaging Details:||New Wooden drum, reel, circle, or according to customers request.|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||200 tons per day|
|Name:||ACSR Aluminum Conductor Steel Reinforced||Wires:||7stranded|
|Insulation:||Bare Conductor||Type:||Rose Iris Conductor|
ASTM ACSR Aluminum Conductor Steel Reinforced,
Iris ACSR Aluminum Conductor Steel Reinforced,
Rose ACSR Aluminum Conductor Steel Reinforced
ASTM ACSR Aluminum Conductor Steel Reinforced Rose Iris Conductor
Introduction of ACSR Aluminum Conductor Steel Reinforced
1) Concentrically stranded conductor consisting of one or more layers of aluminum alloy 1350-H19 wires around a stranded steel core
(2) Meets or exceeds industry requirements per ASTM specifications B230, B232, B498, B500, B502, B606, B802, B803, B957, and B958
(3) Steel core corrosion protection from galvanized, aluminized (AZ), or zinc-5% aluminum mischmetal alloy (Zn-5Al-MM) coatings with aluminum cladding (AW) is also available
(4) Steel core is available in Standard, High, Extra High, and Ultra High strengths
|Code||Size (AWG/MCM)||Number of Strands(mm)||Weight(kg/km)||Rated Strength(kg)|
Conductor(AAC and ACSR) have been widely used in power transmission lines with various voltage levels,because they have such good characteristics as simple structure,convenient installation and maintenance,low cost large transmission capacity.And they are also suitable for laying across rivers valleys and the places where special geographical features exist.
(1). The permissible long-time operating temperature for aerial conductor is 70℃.
(2). Under the circumstance that rare climate is occurring and ice coverage rate low in heavy ice area, the biggest stress of cable at the lowest point of the sag should not exceed 60% of the short-time destructive power.
(3). When connecting conductors, the conductor beside the connecting tube cant be prominent. Otherwise, the force on the operating conductors will be unbalanced. After connectors are install, the connecting tube should be painted by moisture-proof varnish in order to protect it from corrosion.
(4). Under installation, the arc downing stress of all the conductors should be the same. With in the permissible distance of crossing buildings or dropping to the ground, the stress can be 10-15% higher than regular stress.
Contact Person: Alex Yang