|Place of Origin:||Henan|
|Minimum Order Quantity:||1000M|
|Packaging Details:||New wooden drum, Reel, Circle or according to customer's request|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||200 tons per day|
|Name:||AAC Conductor||Conductor Material:||Aluminum|
|Application:||Power Transmission Lines||Standard:||ASTM,BS,DIN,AS/NZS,IEC, CSA|
|Supplier By Area:||Asia,South America,South Africa||MOQ:||10KM|
|Size:||16MM2 - 800MM2||Type Of Conductor::||Stranded|
800MM2 AAC Conductor,
16MM2 AAC Conductor,
Power Transmission AAC Conductor
16MM2 - 800MM2 AAC Conductor In Power Transmission Lines
Overhead transmission and primary and secondary distribution.
IEC61089, ASTM B231, AAC BS215
Aluminum 1350-H19 wires, concentrically stranded
Conductor (AAC and ACSR) have been widely used in power transmission lines with various voltage levels, because they have such good characteristics as simple structure, convenient installation and maintenance, low cost, large transmission capacity. And they are also suitable for laying across rivers valleys and the places where special geographical features exist.
2. Service Performance
(1).The permissible long-time operating temperature for aerial conductor is 70oC.
(2).Under the circumstance that rare climate occurs and high ice coverage rate, the biggest stress of cable at the lowest point of the sag should not exceed 60% of the short-time destructive power.
(3).When connecting conductors, the conductor beside the connecting tube can’t be prominent. Otherwise, the force on the operating conductors will be unbalanced. After connectors are installed, the connecting tube should be painted by moisture-proof varnish in order to protect it from corrosion.
(4).Under installation, the arc downing stress of all the conductors should be the same. With in the permissible distance of crossing buildings or dropping to the ground, the stress can be 10-15% higher than regular stress.
We can supply this conductor according to different recognized standards, such as IEC61089, BS215, BS EN 50182: 2001, STM B231, CSA C49, DIN480201, JIS C3109, customer special specification also can be satisfied.
|Stranding &wire diameter||Approx Overall diameter||Breaking Load||DC Resistance at 20||
Contact Person: Alex Yang
PVC XLPE PE Insulated B-232 B-500 Aluminium Conductor Cable
High Voltage Waterproof Black ABC XLPE Aluminium Cable
Underground BS 215 Bare 95mm AAC Ant Conductor
Multi Core 200mm2 37/5.23mm AAC Tarantula Conductor
Combined Light Weight ASTM DIN AACSR Conductor
Silver Coated Steel Core AACSR 0.6/1kv Overhead Aluminum Wire