|Place of Origin:||Henan|
|Brand Name:||Sanwu Cable|
|Minimum Order Quantity:||1000M|
|Packaging Details:||New Wooden drum, reel, circle, or according to customers request.|
|Payment Terms:||L/C, T/T, Western Union, MoneyGram|
|Supply Ability:||200 tons per day|
|Product Name:||Aluminum Conductor Steel Reinforced||Original:||Henan, China|
|Voltage Rated:||0.6/1kv||Application:||Overhead Transmission Line|
Low Voltage Aluminum Conductor Steel Reinforced,
Overhead Transmission ACSR Conductor,
ISO Aluminum Conductor Steel Reinforced
Low Voltage Aluminum Conductor Steel Reinforced Overhead Transmission
Application of Aluminum Conductor Steel Reinforced
Aluminum Conductor Steel Reinforced have been widely used in power transmission lines with various voltage levels,because they have such good characteristics as simple structure,convenient installation and maintenance,low cost large transmission capacity. And they are also suitable for laying across rivers valleys and the places where special geographical features exist.
Installation of Aluminum Conductor Steel Reinforced
It is recommended that the installation instructions indicated by the Local Electric Code, or any equivalent, be followed, so that the safeguarding of persons and the integrity of the product will not be affected by deficiencies in the installation.
|Code||Size (AWG/MCM)||Number of Strands(mm)||Weight(kg/km)||Rated Strength(kg)|
(1). The permissible long-time operating temperature for aerial conductor is 70℃.
(2). Under the circumstance that rare climate is occurring and ice coverage rate low in heavy ice area, the biggest stress of cable at the lowest point of the sag should not exceed 60% of the short-time destructive power.
(3). When connecting conductors, the conductor beside the connecting tube cant be prominent. Otherwise, the force on the operating conductors will be unbalanced. After connectors are install, the connecting tube should be painted by moisture-proof varnish in order to protect it from corrosion.
(4). Under installation, the arc downing stress of all the conductors should be the same. With in the permissible distance of crossing buildings or dropping to the ground, the stress can be 10-15% higher than regular stress.
Contact Person: Alex Yang